Active Fire Protection v’s Passive Fire Protection
To understand why we need to look at the differences between the two. Active Fire Protection are products such as Fire Detection Systems and with Fire Suppression provides a way of not only detecting the fire but also suppressing it until the Fire Service arrive.
Passive Fire Protection uses products such as Firestopping, Intumescent Seals and Boards whereby the integrity of the room is maintained or enhanced by the installation of the these products. This ensures that if a fire does occur that it is contained for a set period of time or in some cases protects the integrity of the structure such as structural steel work protection.
But having one without the other compromises the level of coverage. If a room has Active Fire Protection using Fire Detection and Suppression the fire would be detected and suppressed, but may re-ignite again if the integrity of the room has not been maintained using Passive Fire Protection products. Many designers forget or don’t realise that any air gaps in the infrastructure of the room will allow not just the gas to escape but also oxygen to re-enter the room. Poorly fitting boards, entry points for cable and pipes as well as poor fitting doors and windows can all contribute to a leaky room.
For Passive Fire Protection, if a room is only protected by Passive Fire Protection then a fire will be contained for the period of time specified but the damage to the room and it’s contents will be substantial. If the equipment in the room is of high value (not just monetary high value) such as data then the detrimental effect on the business would be quite dramatic. The protection of life will have been maintained but the protection of the assets especially within the room will have been destroyed.
So ensure you have both Active Fire Protection where it’s needed as well as Passive Fire Protection.
Concept Fire Suppression Ltd offer Passive Fire Protection services only where there is a Fire Suppression & Detection fitted within the room. When a room is completed a Room Integrity Test is carried to check how well sealed the room is to hold the gas within it at a minimum concentration for at least 10 minutes. This test checks how leaky the room is and many builders and fit-out contractors then struggle to get the room to pass this test. We have therefore partnered with Passive Fire Protection Engineers who will get the room to pass using approved products and we then guarantee that the room will pass the Room Integrity Test.