FM200 – Still going strong!
In our last post we looked at the news that Du-Pont were increasing the price of FM200 and as it turned out it was a very substantial rise approximately 40% per Kg! Although this came a bit of a shock for the industry (me included), as prices have been decreasing over the years, what practical effect has this had?
Well although the cost of FM200 has gone up 40% it hasn’t had quite the impact of pricing itself out of the market yet. All designs we have looked at comparing the cost of the Fire Suppression Agents it still is cheaper than the alternatives of Inert Gas (IG55 & IG541) and Novec 1230, although there isn’t a massive amount of difference especially with inert gas.
As an example, the last design we did which showed all three products Inert Gas was still 10% more expensive than FM200 and Novec 1230 a massive 22% more!! Although this can alter from design to design it looks like Du Pont won’t be dropping the price too quickly.
Although we are in a competitive world, cost isn’t always the answer. There are many advantages and disadvantages to all the Fire Suppression Agents and care should be taken to ensure lower installation costs don’t turn into higher on going costs.
As a brief overview of the three main products we use in commercial Fire Suppression Applications such as server rooms, data halls and switch gear rooms please see below for some of the main advantages and disadvantages. If you would like to know more on a particular product then click the product name or contact us directly.
There are many advantages and disadvantages for all three products, but the main ones are:-
Efficient Storage (stored as a liquid)
Tried and Tested
The least environmentally friendly of the three
Comes under “F Gas” Regulations
Cylinders usually need to be distributed throughout the room
Cylinders can be located away from the room
The ultimate environmental product
Multiple rooms can be protected by one bank of cylinders
Requires many more cylinders than FM200 or Novec 1230
Always requires Over Pressure Vents
Requires more nozzles
Better environmental credentials than FM200
Requires less cylinders than Inert Gas
Requires less nozzles
Requires larger pipework than FM200
Cylinder must be located very close to the room
Requires more agent than FM200
There are of course many other advantages and disadvantages but these are just a few. We find that many clients already have a pre-conceived idea of what each product does based on what the last company they spoke to wanted to sell them!
At Concept Fire Suppression we like to give a complete picture to ensure you get the best solution to your problem
If you want more information then contact us directly, by phone or e-mail.